SCP Cat6-S-WT 1000' Cat6 Siamese Network Riser Rated Cable 4 Pair 23AWG SBC UTP CMR PVC Jacket White
Siamese Category 6 at 550 MHz Ethernet Dual Cable in a Pull-Box for Businesses and Home Networks alike. This 23AWG / 4 Pair Siamese Cable Features Solid Bare Copper UTP CMR Rating (Non-Plenum Riser), UL Listed and meets or exceeds EIA/TIA 568 B.2-1, UL, CSA and ISO/IEC 11801 specifications. White Low Smoke PVC with a Rip Cord and Sequential Footage Surface Print Makes Long Run Installation a Snap. Especially Designed for Indoor Installation.
Conductor: 23AWG Bare Solid Copper
Insulation: Solid Polyethylene
ETL Verified to ANSI/TIE/EIA568A
10 Base-T (IEEEE802.3)
Token Ring (IEEEE802.5)
100 Base-T (IEEEE802.3)
FDDI/CDDI 100 Mbps
ATM 155, 622 Mbps
Note: Cat6 cable is still limited to a maximum of 328 ft (100 m) in length that should include the length of patch cables that interconnect equipment. Cat6 cable performance characteristics and test methods are defined in TIA/EIA-568-B.2-2001. Cat6 solid conductors are for distribution (typically) whereas Stranded conductors are usually reserved for flexible needs such as patch cords and cables. AWG conductor sizing is typically 23, comes in pairs of 4, and UTP (Unshielded Twisted Pair). When using LAN (Local Area Network) cable such as this is used in areas of likely ambient interference that would slow performance from the 550 MHz bandwidth and degrade 1000 Mbps (1000BASE-TX) potential performance, then SHIELDED Cable is recommended and you would then look for the STP moniker that indicates Shilded Twisted Pair. If the cable is run near or in Air handling spaces, then you should check the local building codes pertaining to Plenum cable use as each jurisdiction can be different in definition and guidance. Riser rating is something recommended as a minimum for all interior (in wall) use. CM is for exposed runs and CMX is exteriror rating, though not necessarily UV ray resistant to degradation. CMXT and CMXT are discriptor examples that intonate exterior (X) and flooded (F) or Taped (T) for Underground Use (Direct Burial).